4.5KA RCBO Circuit Breaker,
18MM RCBO Circuit Breaker,
Overcurrent Protection RCBO Circuit Breaker
SONTUOEC Economic type 18mm width residual current circuit breaker is in conformity with the standards of IEC61009.It is 10KA short circuit design ; It can cut off the fault circuit immediately on the occasion of shock hazard or earth leakage of trunkline.Thus it is suitable to avoid the shock hazard and fire caused by earth leakage.It can be used in circuits up to single phase 230V,three phase 400V,50 or 60Hz.
Normal working & installment conditions
1.Ambient temperature: -5ºC~+40ºC, 24 hours average temperature not exceed +35ºC.
2.Installment plance altitude: ≤2000m
3.Gas relative humidity:not exceed 50% at +40ºC, higher humidity allowed at lower temperature.
4.Pollution degree: 2 class
5.Installment condition: Mounted in the place without obvious impact or shock, no dangerous(explosion) dielectric without corrosive metal or damaging isolation gas(conductive dust).
6.Installment method: TH35-7.5 mounted rail, can be installed in distribution board, case or box. Generally mounted vertically. Tilted angle between mounting face and vertical face not exceed ±5°.
7.Mounted Category: II,III class.
|Type(wave form of the earth leakage sensed)||Electronic type|
|Rated current In||A||A,AC|
|Rated voltage||V||AC 230|
|Rated Current :||6,10,16,20,25,32,40A|
|Rated sensitivity I△n||A||0.01,0.03,0.1,0.3,0.5|
|Insulation voltage Ui||V||500|
|Rated residual making and
breaking capacity I△m
|Short-circuit current I△c||A||3000,4500,6000|
(with daily average ≤35℃)
|Installation||Terminal connection type||Cable/U-type busbar/pin-type busbar|
|Terminal size top/bottom for cable||mm2||25|
|Terminal size top/bottom for busbar||mm2||25|
|Mounting||On DIN rail EN 60715(35mm)by means of fast clip device|
|Connection||From top and bottom|
1. Measuring component and buckling component of products is located between enter line end and entrance line end ;
2. Movement characteristic of products can not be changed with outside mechanical tool ;
3.The operating organization has the free function to take off and buckle;
4. Operate part can not be taken down from the shell outer of products ,the shell can not influence the operating organization to work, the accessory group which replace the feelers pressure ,should guarantee the feelers pressure does not change while running .
5. Overall and mounting dimensioned chart.
Wenzhou Santuo Electrical Co.,Ltd. Browse Categories
RCBO Circuit Breaker
RCCB Circuit Breaker
MCB Circuit Breaker
MCCB Circuit Breaker
ELCB Circuit Breaker
Air Conditioning Contactors
Thermal Overload Relay
Electrical Isolator Switch
Contact Person: Mr. Sunny Zhang